ELECTRICAL SYSTEMS (INCLUDING TEMPORARY POWER)
|APPROVED FOR SUBSTANTIAL COMPLETION:
(REQUIRED FOR SUBSTANTIAL COMPLETION APPROVAL BY PPD OFFICE.)
|1||Establish billing account with PPD Business Operations
Request temporary meter(s) from PPD Utility Administration Department
Install temp. meter and accessories
Energize temp. power
|2||Installation has proper depth and slope of 30” below grade
Installation of metalized tape
|3||Design to fit as-built site conditions
Proper wrap of cables inside manholes on porcelain insulators off floor on Hot dipped galvanized or stainless steel hardware.
All cable not in conduit to be fireproofed with approved tape
Grounding and strapping of cables and lid to ¾” ground rod
Square or rectangular spring assist covers
Gravel in switch pit
|24 Hours||Operations Engineer to verify site conditions and approve any field adjustments as required.
Tape should be equivalent to Scotch Brand #7700
|Medium Voltage Switch:|
|4||Gas pressure within range/no apparent leaks
|24 Hours||Provide one tank of extra SF6 gas at time of Substantial Completion.|
|5||Winding conductor type. Copper Only.
Minimum 1 lb PSI pressure shown on gauge.
Verify size and accessories
Verify wiring in meter enclosure
Verify Correct ELSTER / BYRAM Labs meter
|24 Hours||Meter must be installed prior to energizing.
Any questions contact the Electric and Water Metering Technician listed on the UF PPD website under Utilities and Energy Services, Administration and Analysis
|7||Proper grounding and bonding
Labels for all breakers
Bonding of main service
Testing of breakers / certifications
Certification paper on main breakers.
|Interior wiring and lights:|
|8||Check connections for transformers.
Check panel boards
Bonding & Grounding
Ensure all devices have proper covers
Verify specified T-8 lamps and electronic ballasts
Check all equipment for paint damage
Proper type of connectors, coupling, boxes for raceways
Proper strapping of raceways (EMT, conduits)
Labels for panel boards and all equipment ensure schedules/spares are identified.
Panel board covers are “door in door” type. Busses shall be copper.
All receptacles and light switches shall be marked by circuit number using numbered vinyl cloth adhesive markers.
Boxes above suspended ceilings shall be installed facing down. All covers shall have panel board and circuit number
|Exterior Wiring & Lights:|
|9||Ensure all poles are grounded
Mounting wall fixtures
|10||Check Fuel Level
Test start and transfer time
Check operation of day tank pump.
Turn over all test equipment, i.e. oil bottles, etc.
Turn over all test reports
|11||Training for electrical equipment
Instruction for special equipment
Tools or Keys for specialized equipment
Provide 12 sets of specialized tools or accessory equipment needed to operate the specialized equipment.
Multiple inspections required for large projects
Download as WORD Doc